APPENDIX 2 of the Energy Manager Installation & User Guide describes the Evinox HIU integration. Energy Manager Installation & User Guides ENERGY MANAGER SOFTWARE VERSION 2.5.0 Click Here for – Energy Manager Installation & User Guide PREVIOUS VERSIONS ENERGY MANAGER SOFTWARE VERSION 2.3.0, 2.3.1, 2.4.0 Click Here for Energy Manager Installation & User Guide (includes […]
APPENDIX 1 of the Energy Manager Installation & User Guide describes the M-Bus setup. Energy Manager Installation & User Guides ENERGY MANAGER SOFTWARE VERSION 2.5.0 Click Here for Energy Manager Installation & User Guide PREVIOUS VERSIONS ENERGY MANAGER SOFTWARE VERSION 2.3.0, 2.3.1, 2.4.0 200SM075 V1.0 – Energy Manager Installation & User Guide (includes M-Bus) […]
The controller has two buttons next to the green flashing LEDs which are mainly used for set up purposes. The colour of the LED changes and stops flashing momentarily when the buttons are held for the indicated number of seconds. Hold Ο button for 7 seconds, RED LED shown: DATA ERASE !! Deletes viewable data […]
Yes, it is possible to connect to the Controller via WIFI on a PC, Laptop, Tablet or Mobile Phone. Follow the procedure described in this document 200SM086 v1.0 -Energy Manager- Setting the time
Yes, the Yellow banner should be removed when all connected channels have been enabled and verified. This banner should NOT be left visible to the residents of the property. Please review the Installation and User Guide below for instructions to complete this. Energy Manager Installation & User Guides ENERGY MANAGER SOFTWARE VERSION 2.5.0 Click Here […]
WPS is the easiest method to connect the Controller & Display Press and hold the # button on the energy manager for 3 seconds until its LED turns solid Green and release. Press the WPS symbol on the screen of the display. The display will automatically connect to the controller and show the home page. […]
Choose suitable locations for the Energy Manager and Display, ensuring that the data ports on the bottom of the Energy Manager are easily accessible for the end user. This product uses WiFi technology to link the controller to the display. The signal from the Energy Manager should reach the Display within modern houses but solid […]
CT cable length comes as standard at 1.5 metres. CTs with longer cables up to 5 metres can be ordered as required. The maximum length that should be used for a CT connected to the Energy Manager is 5 meters. Cables should not be extended beyond this as it will have an adverse affect on […]
We advise using Belden 9501 or equivalent. CAT5/6 cable should not be used for Power or Pulse connections on the Energy Manager.
To prove the wiring to the Controller for a PULSE input, view the appropriate channel on the display, then apply a momentary short circuit to the terminals of the pulse input channel and energy should registered on the display.